1 Application and Description
For electricity supply in power stations, public networks and industrial plants for indoor and outdoor installation in dry and wet locations, on racks, in conduits and direct burial, if greater mechanical protection required. Also the Nylon sheath provides an excellent protection against termites.
Conductor: Class 2 circular plain copper or aluminium of the type specified in AS/NZS 1125.
Conductor screen: Cross-linked extruded semi conductive screen.
Insulation: Cross-linked polyethylene compound XLPE in accordance with AS/NZS 3808.
Insulation screen: Cross-linked extruded semi conductive screen.
Water-blocking tape: Semi conductive water-swellable tape
Metallic screen: Plain annealed copper wires complying with AS/NZS 1125
Laying-up: Screened cores are laid up in a right-hand direction of lay.
Filler: Non-hygroscopic material
Binder tapes: Non-hygroscopic binder tape
Separation sheath: Polyvinyl chloride compound PVC 5V-90 complying with AS/NZS 3808
Armour: Single layer galvanized low-carbon(mild )steel wires helically applied
Inner sheath: Polyvinyl chloride compound PVC 5V-90 complying with AS/NZS 3808
Nylon Jacket: An extruded jacket of polyamide 11 or 12
Outer sheath: High density thermoplastic polyethylene ( HDPE)complying with AS/NZS3808
4 Technical data
Max conductor temperature(continuous operation): +90°C
Max conductor temperature(short-circuit for5sec): +250°C
Cable minimum installed bending radius: 20 x cable O D. after installation
（ O D. ：In multiples of diameter over the polyamide layer）