CU or AL conductor, PVC or XLPE insulation, Laid up, Copper wire neutral screen, Black PVC sheath,0.6/1 kV to AS/NZS 4961.
(1) Conductor: Annealed Copper or Aluminium Conductor to AS 1125
(2) Insulation: V-75,V-90 or X-90 in accordance with AS/NZS 3808
(3) Screen: Copper wire
(4) The sheath shall be either V-75 or V-90 in accordance with AS/NZS 3808
(a) For cables with cores insulated with V-75 ,Sheath of V-75
(b) For cables with cores insulated with V-90 or X-90, Sheath of V-90
Unless otherwise specified the sheath shall contain not less than1 percent carbon black added during compounding or extrusion.
Two core: Red
Three core: Red, White
Four core: Red, White, Blue
Five core: Red, White, Blue, Black
PVC or XLPE insulated neutral wire screened cables for use in electrical installations including overhead and underground lines.
For use in various situations to supply the main power from the point of supply to buildings, equipment shed, e.g. switch board to main control cabinet, main between floors and buildings, cable cabinet to motor, etc.
XLPE insulation material has better mechanical, electrical, chemical and durability characteristics than PVC.
3.5 kV/5min(in accordance with AS/NZS 1660.3)
（4）Cable minimum installed bending radius
15x cable O.D.