CU or AL conductor, PVC or XLPE insulation, Black PVC sheath,0.6/1 kV to AS/NZS 5000.1.
(1) Conductor:Annealed Copper or Aluminium Conductor to AS 1125
(2) Insulation: V-90 or X-90 in accordance with AS/NZS 3808
(3) Sheath: 5V-90 in accordance with AS/NZS 3808
Two core: Red and Black
Three core: Red, White and Blue
Four core: Red, White, Blue and Black
Two core+Earth: Red , Black, Green/Yellow
Three core+Earth: Red, White, Blue, Green/Yellow
Four core+Earth: Red, White, Blue ,Black, Green/Yellow
Five core: Red, White, Blue, Black, Green/Yellow
Indoors, cable ducts, outdoors and buried in the ground, for power stations, industry and
switchgear as well as for urban supply networks, if mechanical damage is unlikely .
XLPE insulation material has better mechanical, electrical, chemical and durability characteristics than PVC
3.5 kV/5min(in accordance with AS/NZS 1660.3)
PVC Insulation:-10℃~90℃, short circuit temperature 160℃ for 5 sec
XLPE Insulation:-40℃~90℃, short circuit temperature 250℃ for 5 sec
（4）Cable minimum installed bending radius
15x cable O.D.